shall be capable of and configured to sequence the dampers with the mechanical cooling equipment and shall not be controlled by only mixed-air temperature" per section 188.8.131.52.2 air economizers control signal.
For reasons related to construction economy and simplification of the waterside economizer controls
, the chillers were ultimately selected with a condenser water flow of approximately 1.85 gpm/ton (0.03 L/s x kW) and an entering condenser water temperature of 82.5[degrees]F (28.1[degrees]C).
You might also consider a fixed or differential dry bulb rather than enthalpy sensors: "Dry bulb-based economizer controls
are more reliable due to the error potential of enthalpy sensors.
(Be sure to include damper entrance and exit losses when making this selection; these pressure drops will generally far exceed the pressure drop through the damper itself.) Oversizing the return damper has no operational value; the damper will simply throttle to deliver the required return air/outdoor air ratio required by the economizer controls
or the minimum outdoor air controls.
In addition, in order to find an alternative solution for optimal economizer controls
, it is necessary to understand how the optimal high-limit curves are created.
There may also be missing equipment, such as economizer controls
with modulating air dampers that were specified but never installed.
The following is the schematic/ physical layout of the proposed HERV system--Most of the heat recovery systems available on market are either HRV or ERV or ERV without economizer controls
. However it has been found that if HRV used along with ERV has benefits and can be beneficial for a particular weather conditions.
The outside air inlet at the roof was equipped with a minimum outside air damper that was operable for demand-controlled ventilation and an economizer damper that was operable by standard airside economizer controls
. The return air inlets on each floor were equipped with operable dampers to coordinate with economizer operation of the outside air dampers.
Desirable economizer controls
use a dry bulb high limit to enable economizer use only when the OAT is appropriate.
DCV systems can be incorporated into existing HVAC equipment and often times operate in conjunction with existing economizer controls
, sharing the same outdoor air damper (OAD).
Items like optimum start thermostats, economizer controls
, and demand controlled ventilation can be independently prescribed, but a package of measures provides the synergy of addressing common problems together and building installer expertise and efficiency.
However, over-reliance on the added factory quality control and assumptions that all economizer control
sequences are alike, can lead to failure conditions as explained later in this paper.