# circuit testing

## circuit testing

[′sər·kət ‚tes·tiŋ]
(electricity)
The testing of electric circuits to determine and locate an open circuit, or a short circuit or leakage.
McGraw-Hill Dictionary of Scientific & Technical Terms, 6E, Copyright © 2003 by The McGraw-Hill Companies, Inc.

## Circuit testing (electricity)

The testing of electric circuits to determine and locate any of the following circuit conditions: (1) an open circuit, (2) a short circuit with another conductor in the same circuit, (3) a ground, which is a short circuit between a conductor and ground, (4) leakage (a high-resistance path across a portion of the circuit, to another circuit, or to ground), and (5) a cross (a short circuit or leakage between conductors of different circuits). Circuit testing for complex systems often requires extensive automatic checkout gear to determine the faults defined above as well as many quantities other than resistance.

In cable testing, the first step in fault location is to identify the faulty conductor and type of fault. This is done with a continuity tester, such as a battery and flashlight bulb or buzzer (Fig. 1), or an ohmmeter.

Simple continuity test setup

Useful for locating faults in relatively low-resistance circuits, the Murray loop is shown in Fig. 2 with a ground fault in the circuit under test. A known “good” conductor is joined to the faulty conductor at a convenient point beyond the fault but at a known distance form the test connection. One terminal of the test battery is grounded. The resulting Wheatstone bridge is then balanced by adjusting RB until a null is obtained, as indicated by the detector in Fig. 2. Ration RA/RB is then known. For a circuit having a uniform ratio of resistance with lenght, circuit resistance is directly proportional to circuit lenght. Therefore, the distance to the fault is determined from the producer given by Eqs. (1)–(3). From Eq. (3) and a knowledge of total length l of the circuit, once ratio r has been measured, the location of the fault x is determined. (1)  (2)  (3)

Murray loop for location of ground fault

The Varley loop test is similar to the Murray loop test except for the inclusion of the adjustable resistance R. The Varley loop is used for fault location in high-resistance circuits.

An alternating-current capacitance bridge can be used for locating an open circuit as shown in Fig. 3. One test terminal is connected to the open conductor and the other terminal to a conductor of known continuity in the cable. All conductors associated with the test are opened at a convenient point beyond the fault but at a known distance from the test connection. An audio oscillator supplies the voltage to the bridge, which is balanced by adjusting RB for a null as detected by the earphones. Measured ratio RA/RB equals the ratio of capacitances between the lines and the grounded sheath. Because each capacitance is proportional to the length of line connected to the bridge, the location of the open circuit can be determined from Eq. (4). (4)  See Circuit (electricity)

Alternating-current capacitance bridge used in location of an open circuit in one conductor
McGraw-Hill Concise Encyclopedia of Engineering. © 2002 by The McGraw-Hill Companies, Inc.
Mentioned in ?
References in periodicals archive ?
Their topics include strategy-based diagnostics, principles of electrical systems, sources and effects of electricity, Ohm's law and circuits, electrical and electronic components, digital multimeter use and circuit testing procedures, wires and wiring harnesses, batteries, charging systems, and lighting system fundamentals.
VEIKI-VNL has around 60 employees and is a member of the Short-Circuit Testing Liaison, the association of companies for short circuit testing laboratories.
Built around a series of challenges that assesses pure, functional fitness through callisthenic motion using only body weight and simple gear, each Test of Will competitor will have to complete a 4-minute circuit testing his or her balance, speed, agility and power.
With useful interfaces such as USB host and device, VGA for external display or projector, and Ethernet LAN for remote operation, the TDS7104 will find application in a wide range of environments such as electronic circuit debug and circuit testing, design and manufacture, education and training, and automobile maintenance and testing.
The final two weeks were dedicated to characterizing the custom gas flow measurement using Time-of-Flight technology, circuit testing, and optimization.
Therefore, the strong demand for 65/55-nanometer and below wafer manufacturing has prompted testing and packaging companies to expand their capacity to fill orders from upstream manufacturers for wafer bumping, WLCSP (wafer level chip scale packaging) and mixed-signal integrated circuit and high-speed logic circuit testing.
"While we welcome Michael Schumacher back to Formula One, the fact is any form of in-season circuit testing is strictly prohibited, a regulation clearly laid out by the FIA and adhered to by all of the teams," Williams said.
"Any form of inseason circuit testing is strictly prohibited, a regulation clearly laid out by the FIA and adhered to by all of the teams," said Williams in a statement.
These proceedings of the September 2008 workshop include materials presented at all sessions, covering such topics as devices and assembly, memories, magnetic and QCA computing, QCA reliability, circuit testing, and biological fabrication.
Typical plant and machinery suitable for thermal imaging include electrical panels and switchgear; motor brush contact problems; high voltage distribution systems; temperature measurement of critical process components; hydraulic circuit testing; checking the mechanical condition of rotating equipment, such as pumps, motors, fans, blowers and compressors; refractory surveys; and overheated bearings.
It added that other restrictions will be placed on rig testing, design and manufacturing, suspension and brakes, hydraulic systems, bodywork, weight distribution and circuit testing.

Site: Follow: Share:
Open / Close